444 35 46 (444 EKİN)
Another encountered problem of heat exchanger is mixing of two fluids which passing heat exchanger. Mixing problem is the biggest problem that encountered on heat exchangers.
Resmi Facebook hayran sayfamızı beğenin ve gelişmelerden ilk sizin haberiniz olsun!
Müşteri destek hattımız ile siz değerli müşterilerimize 7/24 hizmet sunmaktayız..
Only reason of mixing is the puncture of plates. Such factors like extremely corrosive fluids, expired operation life of the plates, ram pulse of the steam exchangers are the main causes of puncture for the plates. In general mixing problem is not related with gaskets. The only solution of the mixing problem is to remove or change the deformed or punctuated plate. Problem plate may be identified with eye but for the most accurate result penetration test should be used.In penetration test, two different expendable color penetration dye are squeezed into two different side of plate for expension. Expanded dye passes to the other side when finds any hole and changes the colour of the other side with its colour. So that leakage point can be found.Some problems that may be occured as a result of mixing formation are:
E-Bülten aboneliğe kayıt yaptırarak, web site güncellemelerinden ilk sen haberdar ol!..